|Place of Origin:||CHINA|
|Certification:||ISO9001, ISO18001, OHSAS|
|Model Number:||2-61 cores|
|Minimum Order Quantity:||500meters|
|Price:||USD0.1/m to USD 25/m|
|Packaging Details:||Cable can be supplied in any length required.|
|Delivery Time:||3-20 work days|
|Supply Ability:||5000km per week|
|No. Of Core:||2-61 Cores||Application:||Industrial|
|Insulation:||PVC/ XLPE||Sheath:||PVC/ XLPE|
|Rated Voltage:||Up To 600/1000V||Conductor:||Copper|
Up to 600 / 1000V Copper Conductor PVC / XLPE Insulated Braiding Control Cable
1.1 PVC insulated & sheathed control cable is suitable for connecting wires between electric equipment is controling,monitoring loop and including 600V/1000V (A.C.).The product has not only excellent characteristics in electric and mechanical purpose but also in performance of chemical corrosion resistance ,heat-aging ,environmental stress and flame-retardant.The product has simple construction and convenient to use and could be laid with no restriction of different levels.
Our product of PVC insulated and sheathed control cable can be manufactured according to the Chinese standard GB9330-88,which was complied with reference to IEC227 ,IEC 502 and the standards of Germany ,American ,Japan and U.S.S.R for control cable .
1.2 Flame-Retardant control cable
Flame-Retardant control cable is suitable for connecting wires between electric equipments with a special flame-retardant requirement in controling ,monitoring loop and protecting circuit at rated voltage up to 600/1000V (A.C.) .Our flame-retardant control cable ,low smoke halogen free flame-retardant control cable ,low smoke low halogen flame-retardant control cable ,XLPE insulated control cable and XLPE insulated flame-retardant control cable.
2.1 Rated voltage U0/U should be 450/750~600/1000V
U0~valid of the voltage between main insulated conductor and earthing (metal shield ,metal sheath of environment dielectric).
U~vaild of voltage between any two phase conductor in multicourse cable or single core cable system.
when AC.System is applied ,the rated voltage of cables should be at least equal to the nominal voltage of the system .When DC.System is applied ;the nominal voltage of this system should not be more than the rated voltage of the system by 1.5 times.
2.2 The permitting long-term operating temperature of cable conductor should be PVC insulation :70℃
|Application||Suitable for the interconnection in controlling, Protecting and measuring system.|
|Number of Core||2-61cores|
450/750V confirm to IEC 60227-2007
600/1000V confirm ro IEC 60502-2004
|Test Voltage||AC 3000V/5Min for 450/750V, AC 3500V/5Min for 600/1000V.|
90°C for XLPE Insulation
70°C for PVC Insulation
Up to 5core with color.
Above 5core with number.
|Color of Sheath||Black and customer designated.|
|Manufactured standards||IEC 60227-2007 IEC 60502-2004.|
IEC 60228-2004 class 1 , class 2, and class 5.
Nominal Cross-section area: 0.5-10mm2.
Contact Person: Sunny